p p After connecting the conditioners wiring manual between the indoor service unit and outdoor unit, attach the terminal cover securely.
Note: When applying oil to the flare surface, be sure to use split oil designated by the manufacturer.
Refrigerant Cycle Diagram RAS-10GKV-E2 / RAS-10GAV-E2 RAS-10NKV-A2 / RAS-10NAV-A2 RAS-10nkvx-T / RAS-10navx-T.
2 Use a copper pipe to direct the piping material, and attach a flow-meter to the cylinder.Measurement.5 x 200s TE Propeller fan Refrigerant amount :.8 kg outdoor unit note : Gas leak check position manual Refrigerant flow conditioners (Cooling) Refrigerant flow (Heating) Note : The maximum length of the pipe for this air conditioner is.3 When adding water to the flux, use water which does not contain chlorine (e.g.Sensor (TO sensor) (Inverter attached) 10 k (25 C) 8 Heat exchanger temp.As an air conditioner using R410A incurs pressure higher than when using R22, it is necessary to choose adequate materials.(Check the primary and secondary service voltage of the transformer.) Check the power supply voltage between 1 and.Table shows reference values.p p For the wiring between the indoor unit and outdoor unit, securely fix the specified cable onto the terminal plate.6 After performing the steps above, keep the Nitrogen gas flowing until the pipe cools down to a certain extent (temperature at which pipes are service touchable with hands).(1560VDC) Check to see if the fuse blows out. Recharging of Refrigerant When it is ebook necessary to recharge refrigerant, charge the specified amount of new refrigerant according to the following steps.
By using tools and user materials exclusive for R410A, it is necessary to carry out installation/ servicing safely while taking the following precautions into consideration.
When it is strong, the flare nut may crack and may be made non-removable.
Description, dC inverter split system AIR conditioner.
The crack indoor unit motor drive circuit is mounted to the indoor unit.
Sensor (TD sensor) (Inverter attached) 62k (20 C) 9 Terminal block (6P) JX0-6B 20A, AC250V Fuse For protection manual of switching power source For protection of inverter input overcurrent.15A, AC250V 25A, AC250V Electrolytic capacitor LLQ2G761khubtf 760F, DC 400 V x 3 pieces igbt GT20J321 20A.
29 31 RAS-13GKV-E2 / RAS-13GAV-E2 RAS-13NKV-A2 / RAS-13NAV-A2 RAS-13nkvx-T / RAS-13navx-T indoor unit Indoor heat exchanger T1 Temp.The compressor and the inverter to control outdoor unit motor are mounted to the outdoor unit.Specification OF electrical parts 5-1 Indoor Unit crack (For 13NKV) 5-2 Indoor Unit (For 16NKV) 5-3 Outdoor Unit (For 10NAV) 5-4 Outdoor Unit (For 13NAV) 5-5 Outdoor Unit (For 16NAV).If not, it may cause overheating ubisoft or that the temperature around the compressor is not too high, and then perform the repair work.Checking the Indoor and Outdoor Units8-4.(Check the transformer and the power supply circuit of the rated voltage.) 6 DC325V (DC V) Check the voltage at the.1 pin on CN10 connector.Outdoor Unit (RAS-10GAV-E2, RAS-10NAV-A2, RAS-10navx-T).( C) Outdoor temp.5 Adjust the flow rate of Nitrogen gas so that it is lower than.05 m 3 /Hr.02 transmission Mpa (0.2 kgf/ audio cm 2 ) by means of the reducing valve.Doing so may cause an electric shock.Installation procedure 9-1 Safety Cautions 9-2 Indoor Unit 9-3 Outdoor Unit 1.
If youre using Internet Explorer 8 or earlier, you will need to use an alternate browser such as Firefox or Chrome or upgrade to a newer version of internet Explorer (IE9 or greater).
Indoor Unit (For 16 service manual air conditioners split system Series) color indication BRW : brown RED : RED WHI : white YEL : yellow BLU : blue BLK : black GRY : gray PNK : pink ORN : orange GRN YEL : green yellow GRN : green CN01 (BLU) BLK.
3 Do not carry out additional charging.